cylinder diam 160mm (Overall width 310mm)
Discharge time 12 seconds
Operating temp -30°C to 60°C
Made by Thomas Glover and Company (the sister company of Chubb Fire)
British Standard 5306-8:2012 for the Selection and Positioning of Portable Fire Extinguishers has been updated with an important change
5.4.3 Use of powder extinguishers
The discharge of a powder extinguisher within buildings can cause a sudden reduction of visibility and can also impair breathing, which could temporarily jeopardize escape, rescue or other emergency action. For this reason, powder extinguishers should generally not be specified for use indoors, unless mitigated by a health and safety risk assessment.